Won't using Distributed Power Management to power down a server cause management software to report an error? If so, is there a workaround?
Server management software can indeed report false alarms when Distributed Power Management (DPM) shuts down a server. It's an unintended consequence of some data center monitoring tools like BMC Performance Manager, CA Virtual Performance Management, Microsoft System Center Operations Manager and others. This issue is often overlooked until DPM starts to shut down servers.
The problem occurs because the management software tools are not aware or orchestrating the server's state, so the tool cannot tell the difference between a planned shutdown -- using DPM -- and some other unplanned failure such as a damaged server power supply. As a result, the management tool will typically send major alarms to administrators and perhaps even attempt to invoke other workload balancing actions in response to lost communication with one or more hardware platforms.
Generally, you can take two actions to help integrate DPM with other systems management tools. First, disable any management software alarms generated when a system is powered off using an Advanced Configuration and Power Interface (ACPI) S5 state. If some level of insight is desired, reconfigure the alarm to a low severity where no action is required. Management tools can usually monitor this through the vSphere API. Second, it is highly recommended to flag an alarm when DPM is unable to power-on a server. If the server cannot return from power-off, a serious problem may exist that requires investigation and correction. This can also be monitored with the DrsExitStandbyModeFailedEvent through the vSphere API.
Virtualization has matured to the point where organizations can look past the obvious benefits of static consolidation and take advantage of emerging tools like DRS that can intelligently automate consolidation and computing resource allocation based on workload activity levels. When properly coupled with power management utilities like DPM, virtualization can optimize workload placement and actually shut down idle servers to save the maximum amount of energy -- further lowering the cost of enterprise computing.
Dig Deeper on DRS and DPM
Related Q&A from Stephen J. Bigelow
Full virtualization and paravirtualization both enable hardware resource abstraction, but the two technologies differ when it comes to isolation ... Continue Reading
Organizations can cap their hyper-converged infrastructure costs when they deploy the Azure Stack HCI platform, but once they plug into the cloud, ... Continue Reading
You can implement ESXi on ARM -- or other RISC processors -- in micro and nano data centers. A nano data center is more specialized but also more ... Continue Reading
Have a question for an expert?
Please add a title for your question
Get answers from a TechTarget expert on whatever's puzzling you.